Linjiaba Pump Station is the first station which adopts large-scale gear-driven bulb tubular pump set.In order to obtain optimum hydraulic performance of the pump set,its hydraulic loss was calculated by Computational Fluid Dynamics(CFD),and the results were compared with the model pump set test.The structures of bulb tubular pump supports,vane angle adjustment,main shaft seal apparatus,bearing arrangement,gearbox and synchronous motor were analyzed.The conclusion indicates that,the testing efficiency of the model pump set is 78%,the cavitation characteristic is fine at the net head(2.4 m) of pump station,and its hydraulic performances reach the index of the eastern route project of the South-to-North Water Diversion.The application of large-scale gear-driven bulb tubular pump set provides reference for type selection,design and manufacture of other pump stations of low lift and large flow capacity.
Caridad J,Kenyery F.CFD analysis of electric submer-sible pumps(ESP)handling two-phase mixtures[J].Transaction of the ASME:Journal of Energy Resource Technology,2004,126(2):99-103.
Li Yaojun,Wang Fujun.Numerical investigation of performance of an axial-flow pump with inducer[J].Journal of Hydrodynamics,Ser.B,2007,19(6):705-711.
吕建新,许跃华.大型灯泡贯流泵CFD计算[J].排灌机械,2007,25(5):17-19.Lü Jianxin,Xu Yuehua.CFD calculation for large-scale bulb tubular pump[J].Drainage and Irrigation Machi-nery,2007,25(5):17-19.(in Chinese)
陈松山,严登丰,陆伟刚,等.低扬程水泵装置起动过渡过程分析[J].江苏大学学报:自然科学版,2003,24(5):47-50.Chen Songshan,Yan Dengfeng,Lu Weigang,et al.Analysis on transient process in low-head pumping installation during starting period[J].Journal of Jiangsu University:Natural Science Edition,2003,24(5):47-50.(in Chinese)
张仁田,邓东升,朱红耕,等.不同型式灯泡贯流泵的技术特点[J].南水北调与水利科技,2008,6(6):6-9.Zhang Rentian,Deng Dongsheng,Zhu Honggeng,et al.Technical features of two bulb tubular pumps[J].South-to-North Water Transfers and Water Science & Technology,2008,6(6):6-9.(in Chinese)