Abstract： In order to solve the propblem of the large axial head force caused by high pressure entry,three methods were introduced,adjusting impeller wearing ring diameter,installing vice blades and reducing rotating speed.Adjusting impeller wearing ring diameter and installing vice blades on front cover of impeller can balance axial force of lift pump for 2 500 t/d SWRO,and the structure would be more reasonable if using the way of reducing rotating speed to increase impeller dimension to balance axial force.Based on the seawater desalination processes,the way to ensure the performance parameters of lift pump was introduced.In view of the high pressure entry environment.The combination structure of single-stage cantilever,double volute and three thrust bearing was chosen.Thick shaft and small cantilever ratio were used to improve the stability of the system.Through the operation of 100 h test at higher pressure environment,the lift pump it was found that can maintains good sealing performance by using upstream pumping mechanical seal and has small weal loss because of non-contact section,thus it can reduce the failure of shaft in the high pressure circumstance.
杨尚宝.我国海水淡化产业发展的现状与对策[J].水处理技术,2006,32(12):1-3.Yang Shangbao.Actuality and countermeasures of seawater desalination industry in China[J].Technology of Water Treatment,2006,32(12):1-3.(in Chinese)Stover R L.Development of a fourth generation energy recovery device[J].Desalination,2004,165:313-321.Stover R L.Seawater reverses osmosis with isobaric energy recovery devices[J].Desalination,2007,203:168-175.叶晓琰,杨孙圣,许建强,等.基于CFD技术的高压泵液力端优化设计[J].排灌机械,2008,26(6):31-34.Ye Xiaoyan,Yang Sunsheng,Xu Jianqiang,et al.Optimization design for hydraulic end of high-pressure pump[J].Drainage and Irrigation Machinery,2008,26(6):31-34.(in Chinese)苏立永,潘献辉,葛云红,等.大型反渗透海水淡化工程能耗降低方法探讨[J].工业水处理,2008,28(3):81-83.Su Liyong,Pan Xianhui,Ge Yunhong,et al.Discussion on the way of decreasing the energy consumption of large SWRO desalination[J].Industrial Water Treatment,2008,28 (3):81-83.(in Chinese)Manth T,Gabor M,Oklejas E.Minimizing RO energy consumption under variable conditions of operation[J].Desalination,2003,157:9-12.严敬,谢功耋,张江源,等.国外一种离心泵双蜗壳设计方法的介绍和分析[J].排灌机械,2008,26(6):46-49.Yan Jing,Xie Gongdie,Zhang Jiangyuan,et al.Analysis and brief introduction for a foreign-designed centrifugal pump of double-volute[J].Drainage and Irrigation Machinery,2008,26(6):46-49.(in Chinese)陆伟刚,李启峰,施卫东,等.减小叶轮后盖板直径的轴向力试验[J].排灌机械,2008,26(1):1-5.Lu Weigang,Li Qifeng,Shi Weidong,et al.Experiment for axial thrust of shortened impeller back shroud[J].Drainage and Irrigation Machinery,2008,26 (1):1-5.(in Chinese)王晓彦.新型非接触式机械密封在丙烷泵上的应用[J].润滑与密封,2008(8):43-45.Wang Xiaoyan.The application of new non-contact mechanical seal for propane pump[J].Lubrication and Seal,2008(8):43-45.(in Chinese)